How to Winterize Your Fire Sprinkler System
Winterizing fire sprinkler systems is a critical service needed to reduce the chance of issues associated with damage to piping because of freezing. Without checking your system, cold weather can cause your fire protection system to cease to function – or worse, burst!
Fire Sprinkler System Testing
State Systems suggests the inspection and test of all wet, dry, and antifreeze sprinkler systems before the onset of cold weather. Take the time to inspect your sprinkler systems for the following items.
Items to check for dry, wet, and antifreeze systems
- Verify FDC is not full of water and ball drips are working properly
- Check water storage tank heaters for proper operation where present
- Determine if heat tracing is intact and operating properly – including monitoring systems for heat trace systems
- Visually inspect the integrity of any pipe insulation where provided
- Visually inspect any wet pipe in attic areas to determine if required insulation is in place, or if the insulation has been disturbed
- Remember that 40 degrees F is the minimum temperature allowed on any wet portion of a sprinkler system
Dry Pipe and Pre-Action Systems
- Check all dry pipe and pre-action systems to make sure they are not flooded
- Drain all low point drains – pay special attention to areas outside the building such as the pump room
- Verify & record location of all drains
- Verify proper operation, function and settings for the air compressor or alternate air supply
- Drain condensation from air compressor tank
- Check valve rooms, pump rooms, stair enclosures and areas with exposed piping for the following:
- Heaters are working properly
- Dampers are closed
- No unprotected openings are present
- Many wet sprinkler systems prevent pipes freezing by adding an antifreeze solution to the system. Check the antifreeze systems by testing the concentration of the antifreeze solution. If necessary, adjust the level of antifreeze solution in the systems to prevent freezing. When dealing with anti-freeze systems, reference (NFPA 25, Section 5.3.3) for additional information.
When Should I Inspect My Sprinkler System?
It is important to visually inspect your fire sprinkler system before the onset of cold weather and periodically throughout the winter. After winterizing your system, check routinely for leaks, corrosion, or anything that appears out of the ordinary with your system.
I Live in a Warm Climate – Do I Need to Winterize My System?
State Systems recommends checking your fire sprinkler system before the onset of winter, even if your location experiences mild winters. In fact, buildings in warmer climates can be more vulnerable to freezing because insulating measures are ignored. Without inspecting your system, it can be difficult to properly prepare for the onset of cold weather and whether or not your system is ready. Even one cold snap can bring a system to the breaking point if it has not been properly winterized.
State Systems Sprinkler Winterization Services
State Systems may provide winterization services as a standalone service call or as a part of annual and/or quarterly inspection services agreement. Winterization should always be performed prior to the on-set of cold weather and may be performed by the customer (owner) or by State Systems Technicians or Inspectors.
State Systems’ dedication to succeed in a given task and their willingness and desire to make a difference is a trait that most companies do…Walt Czyrnik Read More